FRP GRP Fiberglass Fume Gas Scrubber System
|FOB Price:||US $100-15,000 / Set|
|Min. Order:||1 Set|
|Min. Order||FOB Price|
|1 Set||US $100-15,000/ Set|
|Production Capacity:||1000 Units Per Year|
|Payment Terms:||L/C, T/T, Western Union, Paypal, Money Gram|
- Model NO.: FRP fume gas scrubber
- Application: Gas
- Pressure: 0.1MPa≤p<1.6MPa
- Pressure Level: Low Pressure (0.1MPa≤p<1.6MPa)
- Trademark: JHR
- Specification: FRP fume scrubber
- HS Code: 392690
- Function: Storage Pressure Vessel, Separation Pressure Vessel, Heat Pressure Vessel, Reaction Pressure Vessel
- Material: GRP
- Storage Medium: Air
- Condition: New
- Transport Package: Standard
- Origin: China
FRP acid mist purification tower
This purification tower adapts to many equipment which are used for disposaling of unhealthy waste gas.
It is not only widely used,but also high effidency of purification(more than 95%)
Tts equipment resistance is low(400-600pa),cost of operation is low
Acid gas:sulfuric acid,HLC,nitric acid,HF etc.
Alkali gas:NAOH,KOH,NHS stc.
We used different absorption solvent for dealing with different harmful gas.
Construction and working theory:
1.Purification tower consists of tower body,solvent tank,praying system,packing,separator of gas and solvent.
2.According to different mediums,purification tower could made of PVC,PP,FRP,carbon steel or stainless steel.
3.Off-gas is input to the tower body from the bottem inlet,then passed through the filing layer and spray mist system.
4.Off-gas is fluid purified,purified gas pass through the gas-solvent separator,is output to atmosphere.
5.Mist spray system takes American HHSJ spray-head,with good nebulization,obvious purification effect.
1.This is purification tower should be installed on anti corrosion basis which is higher 100mm than ground.Pump with acid resistance should be on another anti corrosion basis.
2.This equipment should be installed indoor,in order to prevent cold weather from effecting on equipment and absorption solvent.
3.If here is no PH controlling system,PH of acid or alkali solvent should be checked regularly,and consistency should be adjusted an any time.
4.Spray-head and filing material should be checked regularly,in order to avoid plugging,any problems should be solved immediately